Click on a photo to enlarge.
Installation of ONE cartridge system with 20 Micron sediment and carbon block to break the chloramine bond. Second step is Total Care 2 1054 for removal of hardness and ammonia.
Well water treatment system for up to 100 grains per gallon of hardness. Water hardness was 85 grains/gallon of this install.
Customer wanted off of chlorine for odors in the water. Chemical feed pump was injecting where irrigation water had chlorine in the water. Install IPHS 1054 for hydrogen sulfide control. Now raw water is delivered to irragation and treated water is only for home.
Well water treatment system with extreme sediment, hardness and hydrogen sulfide issues. Water hardness of 85 Grains/gallon. System includes mechnical spin down with blow down. IPHS 1354 hydrogen sulfide/sediment filters down to 5 micron purity and removes smell from water. CSP 1665 4 cu ft softener is used for hardness. Customer is extremely happy with the outcome.
Well water treatment system for up to 45 grains per gallon of hardness. Recommend sanitation of water because it is exposed to atmosphere in the holding tank. Equipment used: Ion Pro 1354 aeration and 5 micron sediment filtration,CareSoft Pro 1665 4 cu ft softener used due large property with 3 dwellings. Water is then sanitized with UV. Water quality for the home is sanitized and soft with 5 micron purity.